Pizza oven venting a Forno Bravo wood fired oven is very straight forward. There are four basic applications that need to be considered.
- Outdoor installation with no overhead obstructions – single wall stove pipe
- Outdoor installation with overhead obstructions – UL103HT double wall chimney pipe
- Indoor installation – direct vent approved – UL103HT double wall chimney pipe
- Indoor installation – Type 1 Hood required
Direct Vent, Single Wall Stove Pipe:
In most cases, where outdoor pizza oven venting is installed away from any structures in a free standing outdoor kitchen, a single wall stove pipe will be sufficient. Forno Bravo ships a standard single wall stove pipe kit in our residential modular pizza oven kit. We use a product called Durablack which is readily available in the US and Canada through distributors of M&G Duravent. Don’t let the name fool you, the stove pipe is stainless steel and a high quality product.
You can extend these stove pipe chimney systems vertically to assist draw or your install design. Forno Bravo doesn’t offer these items in our on line store at this time, but we can assist you in sourcing or purchasing if you would like to call and speak with a customer service representative.
DuraBlack must be installed with a minimum of 18″ clearance to combustible materials. If you have concerns about single wall stove pipe, you can always upgrade to double wall chimney pipe.
WARNING: A major cause of vent related fires is failure to maintain required clearances (air spaces) to combustible materials. It is of the utmost importance that DuraBlack be installed only in accordance with the manufacturer instructions.
Direct Vent, Double Wall Chimney Pipe (UL103HT):
Direct vent chimney system allows your pizza oven venting to draw naturally and perform at the highest level thermally. For indoor pizza oven venting installations, or outdoor installations where your wood fired oven will be under a roof structure such as a pergola, Forno Bravo recommends using a UL103HT listed double wall stainless steel chimney system. We use a product called DuraTech, which is readily available in the US and Canada through distributors of M&G Duravent. Our Casa, Premio, Professionale and Modena ovens have all been UL tested and certified for indoor installation using the DuraTech UL103HT listed chimney system.
DuraTech can be installed up to sixty (60) feet vertically and must be a minimum of three (3) feet above the roof it is penetrating. If you would like to use an offset to change the flue direction to avoid an obstruction, you can use up to two (2) offsets, no greater than 30 degrees each. This means you can do a 30 degree elbow, zero to 48 inch horizontal chimney pipe and then a 30 degree elbow correction back to the vertical. If you need a second correction, you can do another 30 degree elbow with a horizontal pipe and then a 30 degree correction back to the vertical. For a guide on how using an elbow kit will effect your vertical height refer to page 12 of the DuraTech manual.
WARNING: Do not use two 30 degree elbows to create a 60 degree angle as this will void all warranties and present a fire hazard within the chimney system.
Forno Bravo sells DuraTech UL103HT listed products in our on line store. If you let us know at the time your purchase our pizza oven, we can include DuraTech pizza oven venting items in the unit price and save you shipping costs. Also, if you purchase a fully assembled oven, like our Toscana, we can modify it to use the DuraTech chimney system if you plan on putting it under a patio cover.
Type 1 Hood:
Type 1 Hood‘s for commercial pizza oven venting will be required about 50% of the time. This is determined by the local code enforcement. Type 1 Hoods should not be confused with Grease Ducts, which are a different application. Our commercial pizza ovens have all been tested and UL certified for use with a Type 1 hood. Most common reasons a Type 1 Hood might be required, instead of direct vent:
- Your pizza oven venting installation can’t meet the no more than two 30degree bends in the direct vent application;
- Local interpretation of mechanical code by municipality requires a Type 1 Hood;
- Locale is prone to fires and extra precautions are taken;
- Locale doesn’t lend itself to natural draw due to obstructions, natural air pressure, etc necessitating assisted air flow to compensate.
Will a Type 1 Hood effect oven performance? Only slightly, a Type 1 Hood will introduce some draw on the oven pulling heat out, but your fuel cost should only be slightly impacted.
At this time, Forno Bravo doesn’t sell the Type 1 Hood, but we do provide the specification our commercial pizza ovens were tested too.
Always contact your local Building Official or Fire Official regarding permits, restrictions and installation inspections in your area.
General Guidelines for Pizza Oven Venting:
- Allow 18″ of clearance around DuraBlack single wall stove pipe;
- Allow 2″ of clearance around DuraTech double wall pipe;
- A minimum of three (3) feet of stove pipe or chimney below the ceiling is required;
- Chimney’s must extend at least three (3) feet above the highest point where it passes through a roof and at least two (2) feet higher than any portion of a building within ten (10) feet;
- Never fill any required clearance with any insulation or other materials;
- Interior chimneys shall be enclosed where they extend through closets, storage areas, occupied spaces or anyplace where the surface of the chimney can be contacted by persons or combustible materials. The distance between the outer wall of the chimney and the enclosure shall be at least two (2) inches;
Offset Elbow Installation:
- The DuraTech Chimney system may have a maximum of two (2) offsets (four elbows total) of 30 deg from vertical;
- Elbows are manufactured in 15 deg and 30 deg angles measured from the vertical;
- Forno Bravo only offers 30 deg elbows for sale. If you need 15 deg elbows, you can buy directly from a M&G Duravent distributor;
- Avoid elbows if possible as a vertical chimney is the most efficient;
- Do not combine elbows to create steeper angles and never exceed two elbows in one chimney system. A single elbow is defined at 30 degree bend and then a 30 degree correction (one set);
- Refer to Elbow Offset Chart on Page 12 of the DuraTech manual.
Do not use with forced draft, positive-pressure appliances.
If your installation requirement can’t meet these standards, be sure to consult a professional and obtain necessary permits in advance. Feel free to email or contact us directly at 800-407-5119.
Thank you for your interest in Forno Bravo!