If this is your first visit, be sure to
check out the FAQ by clicking the
link above. You may have to register
before you can post: click the register link above to proceed. To start viewing messages,
select the forum that you want to visit from the selection below.
Forno Bravo Forum Thread Message
Hello, Forno Bravo Community Forum Members!
The Forno Bravo team has heard the feedback in regards to the community forum. We wanted to take the time to re-enforce our commitment to a fully engaged Forum with professional moderation.
Our top priority as a company is to fix all forum errors and issues that you are experiencing. As we are swiftly working on these problems, we want to say that we highly value the Forum Bravo Community Forum and every single community forum member.
We have set up this thread so that every member can address any concerns, issues and questions about the forum. Please feel free to ask whatever you would like in regards to the forum; let us know what issues you are experiencing so we can work on resolving them as fast as possible. However, we stress that we would like constructive engagement, so please be specific about the issue you are experiencing.
Thank you for all of your patience and continued support.
Our local building department is asking for the justification of combustion air to the space. Does Forno Bravo have information regarding sizing the combustion air requirements for the Ristornate 160 wood burning oven?
R1006.2 Exterior air intake. The exterior air intake shall be capable of supplying all combustion air from the exterior of the dwelling or from spaces within the dwelling ventilated with outside air such as non-mechanically ventilated crawl or attic spaces. The exterior air intake shall not be located within the garage or basement of the dwelling nor shall the air intake be located at an elevation higher than the firebox. The exterior air intake shall be covered with a corrosion-resistant screen of 1/4-inch (6 mm) mesh.
R1006.3 Clearance. Unlisted combustion air ducts shall be installed with a minimum 1-inch (25 mm) clearance to combustibles for all parts of the duct within 5 feet (1524 mm) of the duct outlet.
R1006.4 Passageway. The combustion air passageway shall be a minimum of 6 square inches (3870 mm2) and not more than 55 square inches (0.035 m2), except that combustion air systems for listed fireplaces shall be constructed according to the fireplace manufacturer�s instructions.
R1006.5 Outlet. Locating the exterior air outlet in the back or sides of the firebox chamber or within 24 inches (610 mm) of the firebox opening on or near the floor is permitted. The outlet shall be closable and designed to prevent burning material from dropping into concealed combustible spaces.
In practice, a standard brick vent behind the fridge should supply the needed air, and avoid drafts and light leak.